I have a Flair system with 6 pucks and 14 vents. It works with a Trane Nexia system as an unsupported thermostat. It was installed about four years ago.
I would like to know how the control strategy works when used with an unsupported thermostat. Our system requires daily adjustments in settings in both the Flair system and the Nexia system. I'd like to get closer to automatic operation but I need to understand your control strategy.
Please sign in to leave a comment.